Cooling with the data center has become our achilles heal in many cases. Historically the folks in IT had relatively nothing to do with heat or cooling management, this was strictly under the purview of the facilities team (after all, if it wasn’t IT gear, it didn’t count). In todays world though the IT team has to get involved, since they are the ones that need to live with (and fix) the problem.
Well the good news is that in most older data centers (older being 10+ years), there are plenty of low hanging fruit to choose from when deciding what project to undertake in order to develop a more efficient cooling environment within the data center.
Over the next few posts I’ll posit 10 of the easy steps you can take to solve, or mitigate the cooling issue at your site.
1. Hot Aisle/Cold Aisle
As one of the oldest techniques in data center efficiency, placing rows of racks back to back and front to front is a simple method to redirect some of the hot air exiting the back of your racks into a common area. Without this configuration the hot air will exit the rack and be pulled into the front of the adjoining row, thus creating hot spots and very poor distribution of cool air. Creating hot and cold aisle configurations can improve air flow and cooling efficiency by as much as 10%.
2. Variable Speed Drives – Variable Frequency Drives
One of the largest consumers of electricity in data centers are the air handlers and/or air conditioners (CRAH’s and CRAC’s). These units have very powerful fans which need to move large amounts of air across the data center floor to the IT equipment. On many older units the fans spin at a continuous rate and the airflow remains continuous, regardless of how much is actually needed (e.g. a mostly empty data center would get the same airflow as a nearly full data center). Unless IT or Facilities teams are diligent, these fans are normally left on one speed all the time, creating a very inefficient environment. Newer CRAHs and CRACs have variable speed drives which can automatically sense temperature variations on the floor and therefor modulate the airflow, and fan speed, accordingly. Sophisticated units allow the synchronization of many units across a data center so the optimal fan speed, air flow, and energy consumption can be achieved. Implementing variable speed drives, synchronized, can reduce energy consumption by up to 15%. Example vendors; Emerson, Schneider Electric, Stulz.
Read Complimentary Relevant Research
Predicts 2017: Artificial Intelligence
Artificial intelligence is changing the way in which organizations innovate and communicate their processes, products and services. Practical...
View Relevant Webinars
How to Live Without Mobile Device Management
This webinar addresses the growing trend of users refusing to have enterprise management of their mobile devices due to privacy concerns....
Comments or opinions expressed on this blog are those of the individual contributors only, and do not necessarily represent the views of Gartner, Inc. or its management. Readers may copy and redistribute blog postings on other blogs, or otherwise for private, non-commercial or journalistic purposes, with attribution to Gartner. This content may not be used for any other purposes in any other formats or media. The content on this blog is provided on an "as-is" basis. Gartner shall not be liable for any damages whatsoever arising out of the content or use of this blog.